Project B610 process control configuration acceptance test procedure [electronic resource].
- Washington, D.C. : United States. Dept. of Energy, 1994. and Oak Ridge, Tenn. : Distributed by the Office of Scientific and Technical Information, U.S. Dept. of Energy.
- Physical Description:
- 178 pages : digital, PDF file
- Additional Creators:
- Westinghouse Electric Corporation, United States. Department of Energy, and United States. Department of Energy. Office of Scientific and Technical Information
- Restrictions on Access:
- Free-to-read Unrestricted online access
- The purpose of this test is to verify the Westinghouse configuration of the MICON A/S Distributed Control System for project B610. The following will be verified: proper assignment and operation of all field inputs to and outputs from the MICON Termination panels; proper operation of all display data on the operator`s console; proper operation of all required alarms; and proper operation of all required interlocks. The MICON A/S control system is configured to replace all the control, indication, and alarm panels now located in the Power Control Room. Nine systems are covered by this control configuration, 2736-ZB HVAC, 234-5Z HVAC, Process Vacuum, Dry Air, 291-Z Closed Loop Cooling, Building Accelerometer, Evacuation Siren, Stack CAMs, and Fire. The 2736-ZB HVAC system consists of the ventilation controls for 2736-ZB and 2736-Z as well as alarms for the emergency generators and 232-Z. The 234-5Z HVAC system is the ventilation controls for 235-5Z and 236-Z buildings. Process Vacuum covers the controls for the 26 inch vacuum system. Dry Air covers the controls for the steam and electric air dryers. The 291-Z Closed Loop Cooling system consists of the status indications and alarms for the 291-Z compressor and vacuum pump closed loop cooling system. The rest of closed loop cooling was tested earlier. The Building Accelerometer system consists of the status indications for the two seismic system accelerometers. The Evacuation Siren system includes the controls for the evacuation and take cover sirens. Stack CAMs cover the alarms for the various building ventilation stack continuous air monitors. Finally, the Fire system covers the various fire alarms now located in Room 321-A.
- Published through SciTech Connect., 09/20/1994., "whc-sd-610-atp--002", "DE95000995", "35AF11201/35AF11202", and Silvan, G.R.
- Type of Report and Period Covered Note:
- Final; 09/01/1994 - 09/01/1994
- Funding Information:
View MARC record | catkey: 14665846