Desiccant-Based Combined Systems [electronic resource] : Integrated Active Desiccant Rooftop Hybrid System Development and Testing Final Report- Phase 4.
- Washington, D.C. : United States. Dept. of Energy, 2005. and Oak Ridge, Tenn. : Distributed by the Office of Scientific and Technical Information, U.S. Dept. of Energy
- Additional Creators:
- Oak Ridge National Laboratory, United States. Department of Energy, and United States. Department of Energy. Office of Scientific and Technical Information
- Restrictions on Access:
- Free-to-read Unrestricted online access
- This report summarizes the results of a research and development (R&D) program to design and optimize an active desiccant-vapor compression hybrid rooftop system. The primary objective was to combine the strengths of both technologies to produce a compact, high-performing, energy-efficient system that could accommodate any percentage of outdoor air and deliver essentially any required combination of temperature and humidity, or sensible heat ratio (SHR). In doing so, such a product would address the significant challenges imposed on the performance capabilities of conventional packaged rooftop equipment by standards 62 and 90.1 of the American Society of Heating, Refrigerating and Air-Conditioning Engineers. The body of work completed as part of this program built upon previous R&D efforts supported by the U.S. Department of Energy and summarized by the Phase 3b report ''Active Desiccant Dehumidification Module Integration with Rooftop Packaged HVAC Units'' (Fischer and Sand 2002), in addition to Fischer, Hallstrom, and Sand 2000; Fischer 2000; and Fischer and Sand 2004. All initial design objectives established for this development program were successfully achieved. The performance flexibility desired was accomplished by a down-sized active desiccant wheel that processes only a portion of the supply airflow, which is pre-conditioned by a novel vapor compression cycle. Variable-speed compressors are used to deliver the capacity control required by a system handling a high percentage of outdoor air. An integrated direct digital control system allows for control capabilities not generally offered by conventional packaged rooftop systems. A 3000-cfm prototype system was constructed and tested in the SEMCO engineering test laboratory in Columbia, MO, and was found to operate in an energy-efficient fashion relative to more conventional systems. Most important, the system offered the capability to independently control the supply air temperature and humidity content to provide individual sensible and latent loads required by an occupied space without over-cooling and reheating air. The product was developed using a housing construction similar to that of a conventional packaged rooftop unit. The resulting integrated active desiccant rooftop (IADR) is similar in size to a currently available conventional rooftop unit sized to provide an equivalent total cooling capacity. Unlike a conventional rooftop unit, the IADR can be operated as a dedicated outdoor air system processing 100% outdoor air, as well as a total conditioning system capable of handling any ratio of return air to outdoor air. As part of this R&D program, a detailed investigation compared the first cost and operating cost of the IADR with costs for a conventional packaged approach for an office building located in Jefferson City, MO. The results of this comparison suggest that the IADR approach, once commercialized, could be cost-competitive with existing technology--exhibiting a one-year to two-year payback period--while simultaneously offering improved humidity control, indoor air quality, and energy efficiency.
- Published through SciTech Connect., 05/06/2005., "ornl/sub-01-4000010402", and Fischer, J.
- Funding Information:
View MARC record | catkey: 23762749